Diesel steam-boiler ICI Caldaie GX-8000
Steam Capacity: 13600 kg / hour
Useful power: 9302 kW
Steam Pressure: 80-140 kgf / cm²
Fuel consumption: 852,5 kg / hour
Net weight: 29000 Kg
Basic complete set
Steam valve train including the following elements:
- steam bleeding valve flow-actuated explosion;
- spring-relief valve;
- 2 level control indicator;
- 2 blocks of shut-off valves and drain indicator.
Pressure measuring block including the following elements:
- manometer with the big dial with and three-way valve according to INAIL;
- pressure switch high;
- safety pressure switch with manual reset.
Feedwater supply system installed on the boiler’s basis, including the following equipment:
- 1 vertical multistage centrifugal pump suitable for 120°C water;
- 1 flow-actuated explosion shut-off valve;
- 1 pump suction filter;
- 2 back-pressure valves.
Blow-off block including the following equipment:
- drain shut-off valve, flow-actuated explosion;
- quick release toggle valve.
Automatic water-level controller with control sensors:
- pump startup controller;
- pump shutdown controller;
- 1st signal alarm indicator and burner blocking in case of low level;
- 2nd signal alarm indicator and burner blocking in case of low level.
Electrical control box, protection category IP 54, 400 B / 3 + H / 50 Hz consisting of the following elements:
- on-off switch;
- pump's power supply breaker (hand/automatic breaker);
- burner switch;
- pump switch 1;
- level control relay;
- 1st signal alarm relay and hand reset in case of low level;
- 2nd signal alarm relay and hand reset in case of low level;
- alarm indicator and high pressure reset button;
- 1st alarm indicator and low-level reset button;
- 2nd alarm indicator and low-level reset button;
- warning horn.
- vertical economizer of the ECXV series;
- condensate tank of the VRC series;
- atmospheric deaerator of the DEG series;
- pressure deaerator of the DEG/P series;
- feedwater treatment unit of ADD;
- drain tank of the BDV series.
* The specified data for a complete set bear informative character and can be changed by approving with the customer.